Wieland Safety Heat Exchanger
Absolutely safe media separation with double wall tube
Wieland Safety Heat Exchangers consist of double-sided structured tubes made of copper Cu-DHP. The double-wall design ensures an absolutely reliable media separation and complies with the safety regulations of many European countries for heating drinking water with refrigerant.
Standard galvanic tin plating of the outer surface reduces the corrosion risk of galvanized steel pipes connected downstream.
|Finned tube no.
Available from stock. Customized design possible on request.
*Refrigerant R134a and ∆T = 25K (difference between condensation and water temperature)
With customized series Wieland Safety Heat Exchanger flex additional flexible designs are available with suitable connecting parts or different tubes like GEWA-safe plain.
On request brazed UNF-Fittings on both tube ends are possible (5/8“-18 UNF; 7/16“-20 UNF).
- Safety through double wall media separation
- High resistance against corrosion
- Hygienic material copper with antimicrobial properties
- Condensation in domestic hot water heat pumps
- Heat recovery of supermarket refrigeration for drinking water
- Max. operating pressure: 35 bar
- Max. operating temperature: + 130°C
Wieland Safety Heat Exchanger is designed with one tube end with protruding inner tube, to install any warning system for leak detection. The gap at the other tube end can be closed by brazing.
To avoid vibration failure, the finned tube heat exchanger should be braced in the tank not only for transportation but also in operation.
As a rule, the finned tube condenser is placed into the bottom part of the hot water tank. Its position may be horizontal or vertical.
The mounting to the storage flange is by means of a hexagon nut, EPDM-seal and hollow disk (included). When fixing the nut, it is necessary to counterhold at the fitting flats. Connected refrigerant pipes should be soldered to the pipe ends and fully absorb vibrations. A muffler should be mounted where the refrigerant vapour enters.
Enameled hot water tanks are usually fitted with magnesium or impressed-current anodes to protect inadequately coated areas of the steel vessel against pitting corrosion. To maintain this protective effect, we recommend the use of insulation sets to ensure electrical separation of the heat exchanger from the storage tank. Retrofitting of hot water storage tanks is possible at any time.
Insulating set FThe insulating set F (for flange mounting) consists of an insulating sleeve and an insulating ring. For an outside seal it is fitted between the heat exchanger and the storage tank flange as shown in the figure. Alternately a sealing from the inside is possible. If the flange is less than 8 mm thick, a distance washer (not supplied with the set) should be positioned between the hollow disk and the hexagon nut. Insulating sets are accessories and are supplied on request, two sets are required per heat exchanger.
* not supplied with the set | max. operating temperature: + 95°C
Responsibility begins with a high standard of quality. As the first company for semi-finished products in Europe, we have been on the path to certified quality management since 1987.
Today, we have DIN EN ISO 9001:2015 certifications for all producing plants, and our testing laboratories in Ulm and Vöhringen are additionally accredited to DIN EN ISO/IEC 17025:2018.
Pressure Equipment Directive
Safety heat exchangers correspond with the Pressure Equipment Directive 2014/68/EU. These heat exchangers are leak-tested with an overpressure of 50 bar. On the refrigerant side, they are cleaned in accordance with DIN 8964, dried, filled with nitrogen and sealed with plastic caps.